Best Price Factory Use Generators with Low Price for Sale
Model No.: LHBG60
More Details About Factory use Generator
|Model Number (Engine Type)||LHBG30|
|Prime Power/Standby Power||24KW/30KW|
|Phase||AC 3-Phase, 4 wire|
|Voltage Stable time||≤1s|
|Engine Capacity||4.33 L|
|Starting System||DC 24V electric motor|
|Cooling method||water cooler|
|Lubricant method||Passive and flying lubricant|
|Power Factor||0.8 lagging|
|Colour||According to your request|
|Certification||ISO 9001:2008, CE|
|Warranty||1 year or 1000 running hours arrives first|
|Control system||Automatic alarm system|
-------------------------Requirements For Biogas Genset
Within 1m from pressure regulating valve of gas intake
Δ Gas% tempertaure ≤ 40ºC
Δ Pressure 3-20kpa, rate of pressure changing ≤ 1kpa/min
Δ H2S ≤ 200mg/Nm3
Δ Nm3 ≤ 20mg/Nm3
CH4 content ≥40%, changing rate ≤ 2%/min
Δ Impurity particle size ≤ 5μm, impurity content ≤ 30mg/Nm3
Δ Moisture content ≤ 40g/Nm3
Δ Breeding enterprise-biogas generate power
Δ Industry-alcohol plant, starch factory anaerobic sewage treatment.
Δ Refuse landfill-sewage biogas generate power.
------------------------ Company Profile
Δ Established in 2008
Δ Factory area over 40000 square meters
Δ Over 260 employees, technicians over 100 people
Δ Provide repaire service free during the guarantee period
Δ Got the CE, ISO14001, ISO9001 certification
Δ Established cooperation relationship with Cummins
Δ Website www.Lvhuandongli.Com
Δ Strong structure & Strengthen accessories
Δ Easy Start & ATS system
Δ Auto voltage regulation & Stable working condition
Δ Imported and easy-operation control system
Δ Imported and accurate gas control system
Δ Standard parts for easy maintain
Δ long life operation and low-operation cost
Notice About Power Plant Construction ! ! ! ! ! ! ! ! ! ! ! ! !
× Generator Room is usually constructed in open or semi-open type. The floor should be easily to clean and not easily to spark.
× If you want to construct Closed Generator Room, you must construct a single storey building. The open direction of all the doors and windows must turn outside. Please install some big capacity displacement device to avoid gas gathering.
× Generator Room and the Operation Room must be separated, can not be directly connected. The observation window should be with double deck glass protected by steel wire mesh.
× Lightning arrester is necessary.
× Prepar enough fire extinguishing appliances.
× "NO FIRE" mark should be obvious, open flame in the generator room is not allowed.
× In the exhaust gas, there are combustible gas. So, the exhaust pipe of the generator must be leaded to outside of room. The exhaust pipe must be connected tightly.
Contact us if you need more details on Factory Use Generator. We are ready to answer your questions on packaging, logistics, certification or any other aspects about Low Price Genset、New Condition Generator Set. If these products fail to match your need, please contact us and we would like to provide relevant information.
Product Categories : Biogas generator set